NOTE: All references taken from NFPA 99 – 2012 edition We get this question from customers with medical gas manifolds installed outdoors sometimes. NFPA 99 addresses this question directly in chapter 11 where it talks about protecting gas cylinders stored outdoors: Note: sub-paragraph (3) 184.108.40.206 Cylinders stored in the open shall be protected as follows: […]
About Cary Darden
This author has yet to write their bio.Meanwhile lets just say that we are proud Cary Darden contributed a whooping 26 entries.
Entries by Cary Darden
When you have a hospital of any age it is likely that you probably have outlets manufactured by more than one company. When this happens you may get outlet repair parts mixed up especially in the case of Amico and Beacon (Series B) style outlets. If you’ve ever rebuilt the latch valve of one of […]
There are two types of zone valve references that address labeling in NFPA 99 (2012 edition). One is for new construction projects which is located here: 220.127.116.11.8 Zone valves shall be labeled in accordance with 18.104.22.168. 22.214.171.124 Shutoff Valves. 126.96.36.199.1 Shutoff valves shall be identified with the following: (1) Name or chemical symbol for the specific […]
NOTE: All references are taken from NFPA 99 – 2012 edition There seems to be much confusion over the requirements set out by NFPA 99 for existing facilities vs. those for new construction / renovation work. The 2012 edition of NFPA 99 has done a great deal to clear some of this up. 188.8.131.52 Subsection […]