Medical air is one of the most crucial medical gases serving an NFPA 99 Category 1 facility or space. It is typically responsible for keeping ventilators and blenders running and downtime of any length is simply not acceptable. When work must be performed on the air compressor source, especially within the control panel, power […]
About Cary Darden
This author has yet to write their bio.Meanwhile lets just say that we are proud Cary Darden contributed a whooping 27 entries.
Entries by Cary Darden
NOTE: All references taken from NFPA 99 – 2012 edition We get this question from customers with medical gas manifolds installed outdoors sometimes. NFPA 99 addresses this question directly in chapter 11 where it talks about protecting gas cylinders stored outdoors: Note: sub-paragraph (3) 22.214.171.124 Cylinders stored in the open shall be protected as follows: […]
When you have a hospital of any age it is likely that you probably have outlets manufactured by more than one company. When this happens you may get outlet repair parts mixed up especially in the case of Amico and Beacon (Series B) style outlets. If you’ve ever rebuilt the latch valve of one of […]
There are two types of zone valve references that address labeling in NFPA 99 (2012 edition). One is for new construction projects which is located here: 126.96.36.199.8 Zone valves shall be labeled in accordance with 188.8.131.52. 184.108.40.206 Shutoff Valves. 220.127.116.11.1 Shutoff valves shall be identified with the following: (1) Name or chemical symbol for the specific […]
NOTE: All references are taken from NFPA 99 – 2012 edition There seems to be much confusion over the requirements set out by NFPA 99 for existing facilities vs. those for new construction / renovation work. The 2012 edition of NFPA 99 has done a great deal to clear some of this up. 18.104.22.168 Subsection […]